Coolerado H80: Overview of Operation
Coolerado’s hybrid system couples indirect evaporative cooling with two stage vapor-compression cooling. The indirect evaporative cooler can operate alone or it can act as a pre-cooler for the vapor-compression system. When the compressor operates, exhaust from the indirect evaporative cooler is used for condenser cooling. The indirect evaporative cooler used for the system is an integral device with multiple air pathways that exchange heat and mass to cool supply air without the addition of moisture. Motorized dampers control the balance of outside air and return air, and the system operates with a minimum outside air fraction of approximately 45%. Variable speed supply fans for both supply and exhaust allow enable part load operation when only a fraction of the full load capacity is needed.
Coolerado H80: System Data
Nominal Capacity: 5 tons - 8 tons
Operating Weight: 1,550 lbs.
Dimensions (L/W/H): 122”/72”/55”
Electrical Supply: 230 V / 1ph / 60 hz
Supply Airflow: 1,800 cfm, variable speed
Ventilation Airflow: 45-100% OSAF
Airflow Configuration: Vertical return inlet, vertical supply outlet
1. Economizer (100% outside air)
2. Indirect Evaporative (45%-100% outside air)
3. Indirect Evaporative Cooling + Stage 1 DX
4. Indirect Evaporative + DX (45%-100% outside air)
Summary of Performance
The Coolerado H80 was tested for Western Cooling Challenge certification at the National Renewable Energy Laboratory, in Colorado. The results show outstanding performance, indicating that the H80 could outperform federal standards for conventional equipment by 65%. The figure below provides some key information about system performance in each operating mode and at each Cooling Challenge test condition. The results are compared to performance at these conditions for a similarly sized conventional rooftop packaged unit.
Coolerado H80 Documentation
NREL Laboratory Tests for Coolerado H80
Coolerado H80 Product Information
Coolerado H80 “How it Works”
Coolerado H80 Sequence of Operation
H80 Field Test Results